Jam Aqua Alarm
CDBi-485 Zone Detector Module
Field detector module for connection to the detection cable.
It is made of stainless and ABS plastic.
LED on the module and internal alarm sound to give local alarm indication.
For connection to the I-Zone Mini control panel.
'Aqualarm' CDBi-485 Zone Detector Module, one purpose ABS
Box, housing of the electronic circuit. A locking line socket at one end of the module
It is installed to allow the connection of the detection cable. The other end is equipped with cloths
For connection to the PCB. There is a red LED at the top of the module. The
The red LED will flash to indicate an alarm condition. Alarm status and monitoring
Single RS485 connection to the I-Zone Mini control panel.
The module comes complete with a End-to-End Resistor Plug;
Normal operating voltage: 12 volt dc
Quiescent Current: <10mA. Per detector.
Alarm Current: <100mA. Per detector.
Detector Oscillator frequency: 6kHz
Recommended connecting cable: 4 Core Cable 22AWG
Screened Twisted Pair Belden Ref 8723
Line voltage drop: 1.5 mV / m.
Approvals: BS EN ISO 9001: 1994
EMC Directive 89/336 / EEC
CD-X Detect Cable
Cable detection for all models of the control panel. Constructed of hard-worn Helegaine 66 nylon extinguishing arms providing greater protection against dust and conductive contamination.
Locking plugs and sockets for a secure connection.
Available in modular lengths of 1, 2, 5 and 10 meters.
For connection to Detector Modules and Placement equipment.
'Aqualarm' water leak Detection Cable, two flat tinned copper
The braids are separated and protected with Helegaine self-extinguishing nylon 66 sheath.
This type of configuration protects the sensing centers against dust, others
Conductive contamination types and mechanical damage. Cable available
In modular lengths of 1, 2, 5 and 10 / m. Each cable is pre-terminated with a male
And female locking line plug and socket.
When a liquid leaking from the piping needs to be protected, the Detection Cable
It should be fixed with cable ties under the pipeline, then steam
Gasket or thermal protection installed or fixed in the floorboard
Just below the pipeline, using appropriate clips or ties.
Where protection is required from a liquid leaking from equipment, e.g. water-cooled
Computers, chiller factory, air conditioning units etc. Detection Cable for
It is fixed on the floor around the equipment.
Cable Voltage: No greater than 2 volts from DC
Cable diameter: 8 mm
Maximum Detection Cable length:
Reconstruction System: 50 / m (including bridge cable).
ZLM-500: 500 / m (including leader / jumper cable)
Operating temperature range: +1 degrees C to +85 degrees
Construction: Self extinguishing polymer 66
Monofilaments according to ISO 3795
Braid with straight canned copper sensing veins.
Color: Gray / blue
Approvals: BS EN ISO 9001: 1994, EMC Directive 89/336 / EEC CE